Small Gas-turbine power plants
According to a Russian Federation Govern- ment executive order a program “Energy strategy of Russia till 2030” has been em- braced. The most important strategic land- mark for long-term state energy policy is the energy efficiency improvement of Rus- sian economy. In order to improve energy efficiency of industry and in housing and utilities field it is necessary to implement in- novative cogeneration types of power pro- duction based on modern aviation technol- ogies. BLMZ started preparations for the produc- tion of small gas-turbine power plants. GTES 0,3-300 and GTES 0,7-300 are modu- lar, eco-friendly system for the production of electrical and heat energy. This systems need minimum of maintenance. Gas-turbine operated electric generator has an electronic control system and makes it possible to pro- duce energy according to GOST 13109-97.
Summary characteristics of GTU “Soyuz”
|Characteristic||GTE-0.3- 300||GTE-0.7- 300||
GTE 30- 300
|1||Nominal power, kW||250||700||650||30 000|
|2||Electrical efficiency at nominal rating, %||32||23||32||36|
|3||Efficiency of cogeneration cycle, %||84||83||83||84.6|
|4||Air flow at input, kg/s||2||4.12||4.12||105|
|5||Fuel consumption, kg/h||65||262||188||6020|
|6||Appointed hour value, from||60 000||100 000||100 000||100 000|
|7||Structural features||Heat ex- changer||Waste- heat recovery unit||Heat ex- changer||Waste- heat recovery unit|
GTES can work together with public switched network or with other sources of electric power. GTES can operate as a back-up, emergency or main power source. Several GTESs can be united in a single power complex. GTES can be manufactured for different microclimatic areas. The customer can choose the type and performance category of GTES depending on his needs. Waste-heat recovery ofgas-turbine engine gives a lot of possibilities for building heating and managing of certain climate in buildings, for the use of technological processes of industrial companies as well as for the production of cold.